How to Install a Reverse Float Liquid Level Gauge on a Polyethylene Tank
In this video, we will review the steps required to install a reverse float liquid level gauge on a polyethylene storage tank.
Step 1: Lay Out the Parts
Parts for the reverse float liquid level gauge include:
Internal perforated sewer pipe
Float with rope attached going to top of sewer pipe
External clear pipe
Internal pipe support
External horizontal pipe*
Since none of the parts are glued together, the only tool needed is a Phillips head screw driver.
*This pipe can be modified in length to fit your specific needs. A reciprocating saw can be used to cut the pipe.
Step 2: Connect Internal Pipe Support
The internal pipe support is used in SAFE-Tanks or when a bolt through the tank sideway is not desired to support the piping.
A reducer is already installed in the center of the support to fit the pipe size ordered.
The bolts on the bottom of the support can be adjusted with a 3/4’’ box wrench to achieve a level surface on the bottom of the tank.
The pipe itself doesn’t need to be glued. Simply set it in and press down.
Step 3: Install Internal Pipe and External Horizontal Pipe Assembly
If it’s safe and feasible to enter the tank, one person can go in and install the pipe on the back side of the tank. If not, two people can use the rope and rig the pipe over to the horizontal pipe assembly.
Next, feed the rope through the horizontal pipe assembly and connect the component parts:
Elbow with pulley
Roller pulley elbow
Now you’re ready to put the rope clamp on the rope.
Step 4: Assemble External Indicator and Rope Clamp
Pull the indicator through the rope.
Measure off one to one and a half inches below the bottom of the roller elbow.
Assemble and connect rope clamp to visual indicator.
Install external clear pipe. Make sure the rope is running smoothly before connecting. Give the rope a couple good tugs first.
Slip the clear external pipe inside the elbow.
For additional information on chemical storage tank accessories or to schedule a service appointment please contact our field service department.
- February 27, 2014
- Topics: Fittings and Accessories
About Poly Processing
Posts By Topic
Tech Talk Podcast Episodes
Subscribe By Email
- PPC Installation, Operation, and Maintenance to Prevent Chemical Corrosion
- Preventing Cross-Contamination in Multi-Product Chemical Storage Tanks
- Essential Steps for Receiving a Poly Processing Tank
- [Featured in ES&E Magazine] How To Build Cost-Effective Storage Solutions For Wastewater Treatment Chemicals
- Safely Storing Nitric Acid in Crosslinked Polyethylene Tanks: An Essential Practice for the Chemical Industry
Find the recommended tank and system components for your chemical storage challenge.Configure a Tank Package