Proper Venting: Poly Processing Has You Covered
Proper venting of a chemical storage tank system helps ensure safe operation and can also extends the useful life of the tank. Poly Processing Company sees venting as one of the most critical parts of a safe chemical storage system. We also attach venting labels to tanks manufactured at any of our three facilities. Our goal is to give users a peace of mind and walk you through the do’s and don’ts of proper venting in order to keep it simple, safe, and effective for the end users and operators.
Let's examine how we developed our engineered venting program and help you determine the proper venting for your polyethylene chemical storage tanks.
Tank Pressurization Study
Over-pressurization can cause major problems including tank failure. Because of the risk over-pressurization presents, we commissioned a third-party engineering firm to study the impact of pressure on pneumatically-filled chemical storage tanks with different applications or settings.
The findings from the study include:
- The prevailing industry standard regarding venting was to use a vent one inch larger than the fill line. For example, a two-inch fill line requires a three-inch vent. The study determined this industry standard to be adequate if pumped mechanically but not pneumatically.
- Bulk storage tanks are often pumped off a tanker truck using air. As the rate of pumping increases, so too does the chance for a surge of pressurized air entering the tank. That could result in over-pressurization with standard venting.
- Therefore, the thinking in the market shifted. The standard for proper vent size in pneumatically-loaded polyethylene tanks is now at least double the size of the fill line. For example, a two-inch fill line means using at least a four-inch vent. Doing this allows the air to evacuate at a faster rate and reduces the risk for over-pressurization.
- In addition, the study determined that adding length to a vent over three feet with a 90-degree bend will restrict air flow. This affects recommendations on vent size as well as the number and degree of bends in the venting system.
Choosing the Right Venting System
With those findings in mind, here are some guidelines for picking the right venting system:
- While vents add to the initial cost of the tank system, proper venting will help avoid far more expensive occurrences like premature tank failure or even catastrophic failure.
- In addition to standard venting, PPC’s SAFE-Surge manway cover ensures that your tank maintains the proper ACFM at all times, even if the primary venting fails.
- For plastic chemical storage tanks where fumes are not a concern, the F.S. 2650® Manway Cover is a less expensive option for safely handling any air pressure surges.
- The F.S. 2650 Manway Cover combines a vent and manway cover into one engineered lid system that can evacuate air volumes up to 2650 ACFM, which is well within the calculated maximum potential pressure surges resulting using both two- and three-inch fill lines (maximum ACFM from a two-inch standard line is 910; 1150 from a three-inch line).
Poly Processing’s Newest Vent Offering
Until now, space-consuming (and expensive) large vents or multiple vents were necessary to meet venting requirements in order to maintain the warranty. Our solution is an 8” mushroom vent, which is available as a complete assembly in a standalone version. This mushroom vent has been used by Poly Processing Company for several years as part of the F.S. 2650 manway cover. The vent now comes with a flange molded into it so that it can be installed on the dome of the tank to give you greater venting capacity. This is a more cost-effective alternative to many other venting systems.
Like the F.S. 2650, the mushroom vent comes with an HDPE screen to prevent birds from nesting and debris from plugging the vent.
Performance You Can Depend On
All of our tank venting configurations meet or exceed ASTM D-1998 guidelines for tank pressurization. For your specific polyethylene chemical storage system’s proper venting requirements, it’s best to consult with a chemical storage tank expert. For instance, scrubber applications like hydrochloric acid or acetic acid demand an engineered solution to prevent over-pressurization.
Check out additional venting information, including the Poly Processing venting chart.
Our venting chart is based on recommendations and criteria from Venting Design for ACFM Technical Paper. More technical information including the third party study is also available on our site.
Contact a chemical storage tank expert for more information on proper tank venting.
- June 1, 2020
- Topics: Venting
About Poly Processing
Posts By Topic
Tech Talk Podcast Episodes
Subscribe By Email
- PPC Installation, Operation, and Maintenance to Prevent Chemical Corrosion
- Preventing Cross-Contamination in Multi-Product Chemical Storage Tanks
- Essential Steps for Receiving a Poly Processing Tank
- [Featured in ES&E Magazine] How To Build Cost-Effective Storage Solutions For Wastewater Treatment Chemicals
- Safely Storing Nitric Acid in Crosslinked Polyethylene Tanks: An Essential Practice for the Chemical Industry
Find the recommended tank and system components for your chemical storage challenge.Configure a Tank Package