Will Your Chemical Storage Tank Resist Environmental Stress Cracking?
Environmental stress cracking occurs when microscopic cracks form in polyethylene tanks as a result of storing aggressive chemicals. Over time, these imperceptible cracks combine to form larger cracks, which can lead to leaks or even tank failure. If cracks occur, it’s recommended that you replace the polyethylene tank.
In cross-linked polyethylene (XLPE) tanks, tank cracking can possible produce very small leaks over time. In linear polyethylene tanks, mechanical stress can lead to catastrophic failure. If a crack develops due to this stress in an XLPE tank, the cross-linked polymer chains provide a safeguard to help prevent further splitting—unlike potential “unzipping” that can occur in linear polyethylene tanks.
Polyethylene’s resistance to these cracks is called environmental stress crack resistance (ESCR), and it’s a critical factor in the design and testing of polyethylene chemical storage tanks.
How Stress Cracks Occur
Traditionally, when polyethylene is processed, it is done via common plastics processes such as injection molding, extrusion, thermoforming, or blow molding. These processes themselves produce stress because of the pressures, cooling rates, and molecular orientation that are involved in the storage tank manufacturing process. This molded-in stress can result in a possible failure point where the tank is weakest.
In contrast, Poly Processing’s rotational molding creates a virtually stress-free part. However, other factors can lead to environmental stress cracking, such as exposure to harsh chemicals, extreme temperatures, high pressure, and the elements.
You can minimize this risk by choosing the right tank materials and following Poly Processing’s installation and operation guidelines.
Chemicals like soaps, detergents, and wetting agents or surfactants are particularly hard on polyethylene, causing cracking over time. And because polyethylene tanks also expand and contract with the cycling of the tank, they can experience operational stress during chemical discharge or filling.
Fortunately, ESCR tests can validate the strength of a polyethylene tank and measure its resiliency to cracking. These tests ensure that the tank’s materials and composition meet the safety standards necessary for chemical storage tanks.
Environmental Stress Crack Resistance (ESCR) Test
The most common environmental stress crack resistance test is the ASTM method D-1693 for polyethylene plastics. This test determines the susceptibility of a particular polyethylene to stress cracking when storing surfactants. This helps ensure that the polyethylene will perform as it should over time for a safe and durable chemical storage tank.
During the test, ten 1/8th inch-thick samples of compression-molded polyethylene are placed under stress. The plastic pieces are notched to create an imperfection in the samples, and they are bent and inserted into a holding clamp to keep them stressed. The samples are then placed in an aggressive surfactant, at an elevated temperature, and monitored.
Measuring ESCR Test Results
Results are measured hourly. If a sample cracks, it usually cracks perpendicular to the notch. Samples that crack fail the resistance test. Each of the ten samples represents 10% of the sample group. The test is typically stopped when the sample group reaches a 50% failure rate.
The ASTM D-1693 has proven that XLPE has excellent stress crack resistance. It can hold up under pressure with zero failures for thousands of hours. In contrast, linear polyethylene samples typically last less than a hundred hours when tested at the harshest conditions.
Poly Processing’s engineers will work with you to ensure that your particular chemical storage tank will be designed to withstand environmental stress. To properly design a polyethylene tank for your specific application, talk to a chemical storage expert today.
- November 4, 2019
- Topics: Value Added, Tank Design and Materials
About Poly Processing
Posts By Topic
Tech Talk Podcast Episodes
Subscribe By Email
- Using a Universal Ball Dome Fitting on Your Chemical Storage Tank
- PolyBase: A High Performance Tank Pad System for IMFO® Tanks
- Crosslinked Polyethylene Storage Solutions For Your Industry: Part 1
- For Full Discharge, Don’t Rely on Cone Bottom Tanks
- NSF/ANSI/CAN 61: Potable Water vs. Chemical Certification
Find the recommended tank and system components for your chemical storage challenge.Configure a Tank Package